|The graph below shows what is happening. The control is set to start refrigeration if the box warms up to
40 ºF. However when using a pressure control the Cut In, Cut Out and differential are in units of pressures, not temperature. The corresponding pressures must be determined for the refrigerant being utilized and the differential must be wide enough so that the equipment does not short cycle.